5000L/H Water Treatment Plant Reverse Osmosis Water Treatment System 5000L/H Drinking Water Treatment Equipment
Production capacity:5000 L/Hr
Power supply:AC 380V 50Hz
Reverse osmosis (RO)membrane:BW30-400 5pcs USA DOW
Membrane housing:8040pcs 5pcs stainless steel
Raw water pump:CHL8-40/1.5KW
Quartz sand filter,
activated Carbon filter:φ1000 × 1950 FRP 2pcs
Security filter:30 "× 5μm , 9pcs
High pressure pump:CDL8-16/5.5KW 1set
Size (mm):main machine: 3200X900X1800mm
What' s reverse osmosis system?
Reverse osmosis is the most advanded and effective desalting technology. The principle is that under the higher pressure more than the dissolved solution osmotic pressure. Only follow water molecules through the reverse osmosis membrane. Then the solute and solvent separated,thereby getting the purified water. The fine particles,colloid, organic matter, bacteria, virus and 99%the dissolved salt can be removed by the water quality stability etc. already widely used in electronic, electrical, pharmaceuticle,food and other fields.
What's the working principle of the RO mambrane for the reverse osmosis system?
The spiral membrane is constructed of one or more membrane envelopes wound around a perforated central tube.The permeate passes through the membrane into the enbelope and spirals inward to the central tube for collection.
This drinking water purification plant uses mechanical filters,activated carbon filter as a pre-class treatment, the effective removal of suspended solids in raw water, sediment particles , organic colloids,organic matter, odor, chlorine and other impurities, with pre-programmed as a reverse osmosis desalination plant to remove the raw water. Most of the dissolved salts, bacteria, hot stream and so on, to ensure finished water quality standards.
1. Raw water pump-- provide the pressure to quartz sand filter/active carbon filter/softener.
2. Multi-medium filter--get rid of turbidity, suspended matter, organic matter, colloid, etc.
3. Active Carbon filter--Remove the color, smell, free chloride, organic matter, harmful matter, etc.
4. Softener--exchange "ions" of calcium and magnesium with the most common and easiest method.
5. Security filter--prevent large particles, bacteria, viruses into RO membrane, accuracy is 5um,
6. High pressure pump--Provide the high pressure to RO membrane.
7. RO system-- main part of the plant. The RO membrane's desalting rate can reach 99%, removing over 99% ions.